Controls Kits For Power Venters for Gas 30mv Fired Appliances
Proper Control Kits–CK-20FV for Gas 30mv Fired Appliance Applications
Control Kits (CK) control the operation of SWG and CV Power Venters. Control Kits can also control the operation of Field Draft Inducers.
Control kits for gas heating appliances include the CK-20Fv and CK-21. The CK-20FV is used for 30 millivolt gas-fired water heaters and gas-fired pool or spa heaters with a manual or internally mounted thermostat. The CK-21 is used for gas-fired instantaneous water heaters with pressure tap port in the burner manifold.
Control Kits are ETL approved accessories when used in conjunction with the SWG Power Venter.
How Do Thermal Safety Switches Work?
The Thermal Safety Switch detects the increased heat generated by the flue gas spillage and deactivates the furnace or boiler. It will not allow the burner to restart until the switch has been manually reset.
What Control Kit Do I Use For An Oil Burning Appliance?
Refer to the Contractor Reference Guide to select the proper kit for your application.
What is a Thermal Safety Switch or Thermal Cutoff Switch?
A thermal safety switch or thermal cutoff switch is an electrical safety device that interrupts electric current when heated to a specific temperature. These devices may be for one-time use or may be reset manually or automatically. These switches are use on barometric draft controls and draft hoods to detect flue gas spillage and deactivate oil and gas burners. These switches cut off the current to critical heating appliances when a temperature limit is exceeded preventing potential burn out or failure.
|PART #||MODEL||APPLICATION||DRAFT PROVING SWITCH||GAS PRESSURE SWITCH||SECONDARY SAFETY SWITCH||THERMAL POST PURGE||ADJUSTABLE ELECTRONIC POST PURGE||FIXED POST PURGE||DRAFT CONTROL||RJR-6|
|46139961||CK-20FV||All oil-fired systems. Has adjustable electronic post purge.||x||x||x||x|
|46139962||CK-20FV||All oil-fired systems. Has thermally activated post purge.||x||x||x||x|
|46399363||CK-21||All oil-fired systems. (May require optional delay oil valve for simultaneous burner operation.)||x||x||x|